This is the second installment of “Does This Meet Code.” The first installment received many comments, many of which were emailed to me. I encourage to post your thoughts, sarcasm, and code sections in the area listed below the post by clicking on the section called “Comments.”
The question at hand this week looks at an electrical picture sent to us from the the East Coast. This picture was taken during an inspection of a small addition to an existing building. This junction box was utilized to extend several circuits into a the new space. The inspector was not an electrical inspector and questioned “Did you get your final electrical inspection?”
Now, I will never be able to claim to be an elctrical inspector, but where does this fall in the area of incorrect wiring? What if you can’t put the cover on the junction box?
Just a little note, that when you post your first comment on our site, it may take up to 24 hours to “authorize” your comment. This keeps spam off the site.
View previous editions of “Does this Meet Code“