Inspector911 receives many photos from you in the field on odd conditions that you have come across. Believe it or not, there are times that contractors and owners have performed some work that doesn’t really meet code. So we thought of a new section for the site.
As you send us pictures, we will post and look for you all to provide some outstanding comments. Although some pictures may provide some comedy relieve for those of us in the trade, we can really use pictures like this to learn about trends in the field and learn from each other. So if you have a picture and a story to tell for this future section, send us an email at firstname.lastname@example.org
This picture was sent to us from a Building Inspector who was called to perform a rough inspection of the framing. This arrangement is in one of the garages on the project and the yellow flexible piping is for the natural gas piping going to each unit, and the framing is an outside, load bearing wall.
What do you think, does this meet code?